Trane Heat Pump Repair
The A-Quality HVAC Repair Services Team was sent to Mesa, 85207 to repair a Trane HP/HVAC system not heating. Techs found system very low on Refrigerant, causing low pressure switch to trip off. Preformed leak search, finding leak in Evaporator coil. Team made repairs. Replaced coil, and flushed system with nitrogen. Evacuated and recharged, tested for leaks, working properly now !